How do I install the adorne Accent Nightlight?
Click here for detailed installation instructions.
How do I install the adorne Locator Status Light?
Detailed instructions are included with the device. You can also download them here.
How do I install two adorne USB outlets side by side?
Two adorne USB Outlets fit in a standard 1-gang adorne plate. Simply wire each outlet and then snap them side-by-side into an adorne frame. Please note - if you are replacing a single device you will need to pigtail new wire off of the existing wire in order to install two items versus one.
Why can't my adorne GFCI Outlet and adorne USB Outlet fit in the same 1-gang plate?
The adorne GFCI Outlet has a large backbody and cannot be combined with another 1-module item in a 1-Gang, 3-Module Plate.
What is the depth requirement for an adorne Pop-Out Outlet?
The adorne Pop-Out Outlet requires a minimum box volume of 22.5 cubic inches. For the single-circuit plastic box, the minimum depth required is 3". For multi-circuit and metal boxes, the minimum depth required is 3-1/2".
Does the adorne Pop-Out Outlet require a special electrical box?
Most adorne devices fit in all existing NEMA-approved boxes. However, the adorne Pop-Out Outlet requires a minimum 22.5 cubic inch box size for proper installation. Click here for installation instructions.
Can I control an adorne Outlet with an adorne Switch?
Yes, an adorne switch can be used to control an outlet. If you are replacing an existing switch that controls an existing outlet, simply swap it out with any adorne switch.
If you are trying to add a new switch to control an outlet, replace the existing outlet with the adorne Wireless Outlet and then add the adorne Wi-Fi Ready Remote sofTap Switch and connect it to power. Then wirelessly "bind" the switch to the outlet by following the included instructions.