bvseo-msg: The resource to the URL or file is currently unavailable.;
Bazaarvoice SAP Hybris Integration Version 2.8.1
Aluminum housing and side plates, with a steel base and divider, measures 4'' x 5'' x 5 5/8''. Base is configurable to have a combination of two 3/4'' knockouts or two 3/4'' EMT stubs. Accommodates a variety of power outlets (duplex, decorator, GFCI and up to 30A twist lock). Use Wiremold AVIP to provide communications and A/V. Receptacles and wall plates are sold separately.
Large Capacity – The new Wiremold® Lab Bench Table Box can be divided into two gangs that each have the capacity to wire a 15A, 20A, GFCI, or a 30A twist lock receptacle. The LBP2 model Table Box is currently the only third party listed table box that can house back-to-back GFCIs.
Protection against spills – The Wiremold® Lab Bench Table Box is the first lab bench activation to be tested to the proposed UL111 standard for multi-outlet assemblies. This standard includes a spill test, which proves there is no risk of shock or short circuiting due to moisture when combined with certain Pass and Seymour receptacles. See the back of this sheet for the complete list of tested devices.
Multiple Services – The Wiremold® Lab Bench Table Box delivers power, communication or A/V with the use of Wiremold AVIP Series Device Plates. The removable divider, allows designers the option to co-locate services in the same outlet box.
Variety of Mounting Options – Field configurability allows installers to attach conduits directly to the box using 3/4'' trade size knockouts, or use the 3/4'' conduit stubs included with the box.
Listed for Work Surfaces – Meets the NRTL listing for work surfaces as well as UL514A for metallic outlet boxes.
Hi! Is the Lab Bench Pedestal Box offered in a 4-gang?
Asked by: John Desens
The LBP2 series is only available in a two gang option, front and back. We do have the AL241S-HB series which is a four gang lab bench pedestal box. Here is a link for our pedestal table boxes for review, both the LBP2 and AL241S-HB are shown: